Pit C1140304 can be mounted in different kind of hardened surfaces (recommended for areas with setts because of specially designed reinforced flange). Pit C1140302 can be mounted in surfaces hardened with concrete or asphalt
length x width x height x depth
|258 x 258 x 215 x 160
|plastic pit with hardened cover
|260 x 215 x 210 x 110
Inspection pit earth bar for plastic pits C1140302 and C1140304
Pits number: C1140302 and C1140304 can be equipped with equipotential earth bar enables connection of five bus bars (tapes) of max. size 30 x 4 mm. Earth bar fit into the slots provided in the inspection pit.
Cat. no. C1140306
Lubricating medium for couplings of threaded earthing rods
It is used for additional protection of contacts inside coupling. When connecting rods with coupling, we recommend to pour little paste into coupling. It can also be used as lubricating medium for driving stud making it easy to screw it out.
Cat. no. C1130301
Insulating tape for wrapping underground joints
The tape protects underground connections from soil and electrochemical corrosion
CBM Resistivity is fine powder which increases surface area of earth electrode thus reducing resistance to earth. It is being sold in the bags of 25 kg each. Before using it needs to be mixed with Portland cement before using in following proportion:
CBM Resistivity 3 : cement 1
Cat. no. C1070302
Self-adhesive bimetallic divider
The self-adhesive bimetallic divider is used for connecting metals of different electrochemical potentials in a safe manner. It is a copper tape with conductive glue on one side and a protective tin coating. After taking off the protective pad, the divider should be glued to the cleaned surface of a copper-bonded steel tape or a copper flat bar. The tape with the divider glued onto it can be safely connected to galvanized steel or aluminum elements. The divider eliminates the dangerous potential difference and prevents electrochemical corrosion. In case of drilling a hole in the copper-bonded or copper steel tape and using galvanized bolt, the divider should be glued onto both sides of the connected wire. This is to prevent electrochemical corrosion between the bolt head and the copper surface. This action is necessary if we use bolts made of stainless steel.
4 x 5 cm, Cat. no. 1140330(5CM)
4 x 500 cm, Cat. no. 1140330(500CM)